AIR CONDITIONING REPAIR
AIR CONDITIONING REPAIR SERVICE FOR CHILLERS, VRVs, MULTI-SPLITS, CRAC, CRAH & AHUs
We provide a range of Air Conditioning Repair Services for Water Cooled Chillers, Air Cooled Chillers, Dry Air Coolers, Evaporative Condensers, Cooling Towers, Air Handling Units (AHUs), Single-Split, Multi-Split, Variable Refrigerant Volume (VRV) / Variable Refrigerant Flow (VRF).
In addition to this we also provide support in other areas such as Condition Surveys / Dilapidation Reports, Contingency Planning, Temporary Hire Cooling, Critical Spares and Parts Lists.
AIR CONDITIONING REFRIGERANT LEAK REPAIR
Refrigerant Leaks are frequently one of the most common Air Conditioning & Refrigeration faults and we are highly experienced in completing Air Conditioning Refrigerant Leak Repairs on Chillers, VRVs & Multi-Splits and Heat Pumps.
How an Air Conditioning Refrigerant Leak is repaired depends on both the system type and location of the refrigerant leak. For example, some leaks can be repaired without having to remove the refrigerant charge, while others require the full systems refrigerant charge to be recovered to complete the repair. Our engineers are REFCOM CAT1 Accredited Refrigerant Handlers and once the refrigerant leaks location has been identified we can offer recommendations for the repair in line regulations such as the FGas. For more information see our page on Air Conditioning FGas Compliance.
AIR CONDITIONING COIL CLEANING & REPAIR
We have many years experience in repairing Air Conditioning systems Air Cooled Condensers, Water/Glycol Shell & Tube Condensers, Water/Glycol Shell & Tube Evaporators and other Plate Heat Exchangers.
Dirty or blocked Air Conditioning Condenser Coils are a primary cause of high discharge pressure faults and increased electrical power consumption, decreasing energy efficiency resulting in longer runtimes.
During system operation contaminants in the air are pulled through an Air Cooled Condenser Coil. These contaminants become deposited on the Condenser Coils tubes and fins decreasing its ability to reject heat or blocking the surface of the heat exchanger completely.
Our Air Cooled Condenser Cleaning service is designed to remove these contaminants and unblock your systems condenser coils, helping improve system heat rejection and performance. Our experienced engineers achieve this through the use of industry specific high pressure washers, dedicated chemical cleaning agents and/or brushes to get your system operational again.
Over time Water / Glycol contaminants can also buildup within Shell & Tube Condensers, Shell & Tube Evaporators and other Plate Heat Exchangers, often resulting in flow switch faults. Flow switch faults can be caused by a number of factors such as external chilled water / glycol pumps not running, blocked strainers, air in the system, pressurisation unit failure, faulty expansion vessels, incorrect glycol concentration, damaged pump impellers, incorrect inverter pump speeds, faulty water / glycol control valves, faulty pressure transducers, faulty temperature sensors, etc which our engineers check as part of our investigation prior to recommending further invasive repairs.
Within Chiller Shell & Tube Condenser systems water / glycol generally flows through the internal tube bundles, which during normal operation are designed for a given fouling factor to maintain sufficient refrigerant heat transfer. Depending on the frequency and specification of system water treatment over time the water / glycol leaves deposits within the tube bundle that build up, reducing heat transfer and flow rates that impact system performance.
Our Air Conditioning Shell & Tube Coil Cleaning Repair Service removes deposited contaminants and unblocks the tubes, bringing your system back online by improving heat transfer.
Where practicable non-invasive chemical cleaning of the tubes is completed. However, this is not always possible and our engineers are able to remove the condenser-endplates, allowing access to the heat exchanger tube bundle. Each tube is then individually cleaned with brush tipped rods, removing blockages and deposits from the tubes increasing system efficiency.
AIR CONDITIONING FAN COIL REPAIR
We cover all types of Indoor Air Conditioning Fan Coil Unit Repairs. These range from Wall Mounted Units, Floor Mounted Units, Four Way Cassette Units, Concealed Ducted Units to large Centralised Air Handling Units.
Whether your system is tripping on a pressure drop fault due to failed fans, filters, electrical controls or you have water leaks due to faulty condensate pumps, blocked drains pans or drains our engineers we can help.
Following our initial investigation we would also recommend relevant planned preventative maintenance actions including industry specific FCU tasks, filter cleaning and reviewing filter types to reduce the risk of future system failures.
AIR CONDITIONING CONDENSER FAN REPAIR / EVAPORATOR FAN REPAIR
Repairing Air Conditioning systems Air Cooled Condenser Fans or Air Cooled Evaporator Fans are critical to the systems operation and we are experienced in repairing both Axil Fans and Centrifugal Fans.
Air Cooled Condenser Fans are used to remove heat from the refrigerant by pulling lower temperature ambient air across the coil, condensing the high pressure refrigerant gas into a liquid. When Condenser Fans fail it can cause the Air Conditioning system to trip on high discharge pressure fault. Where systems are operating with faulty Condenser Fan Motors or Fan Blades at higher discharge pressures but not in a fault condition, the compressor volume ratio and electrical power consumption is increased reducing efficiency.
Indoor Unit Evaporator fans help boil off the low pressure liquid refrigerant within the evaporator indoor unit by pulling higher temperature air across the coil. Damaged evaporator fans will increase indoor temperatures due to reduced airflow and heat being removed from the temperature controlled space. Depending on HVACR system type they can also reduce the amount of suction superheat back to the compressor, increasing the risk of liquid refrigerant flooding back and damaging the compressor.
During our engineers investigations we determine if the fan motors have burnt out due to things like electrical earth faults, damaged fan blades or impellers limiting airflow, checking the control panel single or three phase electrical contactors and electrical controls.
We then directly source all the necessary replacement parts and fit them to bring your Air Conditioning system back on line. In some scenarios, we are also able to arrange for failed fan motors to be rewired and kept on site as part of clients critical spares.
AIR CONDITIONING COMPRESSOR REPAIRS
Our Air Conditioning Compressor Repair services cover a wide range of hermetic, semi-hermetic and open drive compressors optimised to get your equipment operating. This includes scroll, reciprocating, screw and centrifugal compressor types including magnetic bearing types such as the Danfoss Turbourcor.
Following our engineers investigations we can offer a full range of minor and major compressor repair services. This could range from replacing faulty electrical solenoids, capacity control valves, crank case heaters, temperature sensors, pressure switches, etc to full compressor rebuilds. Should it not be possible to rebuild compressors on site or there is an urgent requirement, we may also able to offer a compressor service exchange.
Where compressor motors have burned out this can produce a chemical reaction between the refrigerant and oil with the system, resulting in high levels of acid that need to be removed as part of the repair. Depending on the Air Conditioning system type, refrigerant, liquid line drier cores and oil often require recovering and sent for disposal to prevent acid recontaminating the new compressors electrical motor windings.
Once the compressor has been repaired or replaced new acid burnout drier cores and oil are added to the system before completing a pressure/leak test/repair. Moisture is then removed from the system before new refrigerant is charged and the compressor load/unload operation checked. The compressor oil is then drained, disposed of and replaced several times to help remove any residual acid from the Air Conditioning system. This is checked using local acid test kits and/or laboratory oil analysis as required. Once all the acid has been removed from the system the refrigerant acid drier cores are replaced with standard moisture removal drier cores and a the system given a final running log before handover.
Participate In Our Research
Subscribe to participate in our research into how Air Conditioning Service Quality Levels Impact B2B Customer Satisfaction & Loyalty Levels Within The UK Commercial Building Services Industry. You can find out more on our page Air Conditioning Service Quality Research.